Accurate compensation: XTSF adopts the 8421 scheme to allocate capacity of each branch;
with the same number of branches, the number of compensation levels
under the 8421 scheme are much higher than that the number under
the scheme of equal distribution of branch capacities.
Excellent harmonic treatment effect: On the basis of the harmonic characteristics of the load,
choose-out of the XTSF series-a suitable product which can suppress
or, in compliance with national standards, filter harmonics.
Fast response: XTSF adopts SCR switching and the response time is less than 15ms.
Switching without impact: XTSF adopted the pre-charge switching technology; thus the
switching current is smooth and does not generate any impact.
The work principle of the low voltage dynamic reactive power
compensation and filtering device is that, through adjustment to
the capacitive reactance ratio, the LC filter is made to form a
very low impedance to harmonics, and as result of such low
impedance harmonics are diverted to the LC filter and the goal of
filtering (or suppressing) harmonics will be achieved. At the same
time, the unit can provide capacitive reactive power to offset the
inductive reactive power of the load and to achieve reactive power
compensation. One device set simultaneously performs the dual
functions of both reactive power compensation and harmonics
filtering (or suppressing).